IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||22 April 2009|
|PDF File Size:||5.47 Mb|
|ePub File Size:||11.66 Mb|
|Price:||Free* [*Free Regsitration Required]|
Selection and application recommendations Status: This standard defines the terms used; defines the quantities to be measured; describes test and measuring circuits which may be used; defines analogue and digital measuring methods required for common applications; specifies methods for calibration and requirements of instruments used for calibration; gives guidance on test procedures; gives some assistance concerning the discrimination of partial discharges from external interference.
Selection and application recommendations Status: Surge arresters containing both series and parallel gapped structures – Rated 52 kV and less This standard applies to all metal-oxide surge arresters with gaps and housed in either porcelain or polymeric housings.
Selection and application recommendations. Your shopping cart is empty. This is a first for arrester standards harmonization. Please note that the selected standard is invalid. Read more 06099-5 SIS Subscriptions. Glossary of terms and iex from IEC publications,, and This standard provides a list of terms and definitions relative to IEC publications from IEC technical committee TC 37 – Surge arresters rss.
We accept all major credit cards American Express, Mastercard and Visa 600099-5, PayPal and bank transfers as form of payment. Subscribe on standards with our subscription service.
IEC RLV | IEC Webstore
Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods. The faster, easier way to work with standards.
Worldwide Standards We can source any standard from anywhere in the world. This standard is not maintained and applies to products not manufactured any longer. IEEE IEEE Standard for Uec Capacitors in Power Systems Capacitors and assemblies of capacitors, insulation means, switching, protective equipment, and control accessories that form a complete bank for inserting in series with a transmission line are applied.
Functional requirements for protective devices are addressed, including varistors and bypass gaps. An additional section discusses several special iiec that may be used to improve lightning performance.
Copyright – ArresterWorks. Preview Abstract IEC Protective equipment for series capacitor banks This part of IEC covers protective equipment for series capacitor banks, with a size larger than 10 Mvar per phase.
BS EN 60099-5:2013
When you use our service you can be assured the latest editions and easy access. Preview High-voltage test techniques – Partial discharge measurements This International Standard is applicable to the measurement of partial discharges which occur in electrical apparatus, components or systems when tested with alternating voltages up to Hz or with direct voltage.
This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC Report error on page.
Search all products by. Also includes details of pollutant compositions and methods of application and the procedures associated with each mode of pollution. This website is best viewed with browser version of up to Microsoft Internet Explorer 8 or Iev 3. The standard is now in your shopping cart. Grounding electrode techniques, pole ground values, and system ground grid values are not addressed or considered in this document.
They irc be associated with other devices such as contactors for idc arrangements.
Click to learn more. The following test report forms are related: Surge arresters and low-voltage limiters for specific use in d. It specifies the procedure for the selection of the rated withstand voltages for the phase-to-earth, phase-to-phase and longitudinal insulation of the equipment and the installations of these 6009-5.
Part 1 covers the insulation surge withstand strength of motors and generators with windings having form-wound multi-turn coils and the 600999-5 of surge protection to form-wound multi-turn coil motors. Sustainable Development Goals and standardisation, how do they connect? The Redline version is not an official document, it is available in English only and provides you with a quick and easy way to compare all the changes between the official IEC Standard and its previous edition.
Protective equipment is defined as the main circuit apparatus and ancillary equipment, which are part of a series capacitor installation, but which are external to the capacitor part itself. In Annex J, some aspects regarding the old type of SiC gapped arresters are discussed. This standard recommends that the selected withstand voltages should be associated with the highest voltage for equipment.
IEC | IEC Webstore
Annexes H and I present comparisons and calculations between old line discharge classification and new charge classification.
What is a standard? It has to be recognized that this application guide approaches the subject of surge protection from ied common or generalized application viewpoint. Artificial pollution testing of surge arresters This standard gives the basic principles of artificial pollution testing of non-linear resistor type valve type surge arresters. Preview Insulation co-ordination – Part 2: